Industrial RO water plant price for 1000 liter per hour for reverse osmosis 500 lph treatment
(1) Raw water Tank: The Raw Water tank store the raw water, it to ensure the stability of water pressure.
The stability of water pressure can prolong the service life of raw water pump.
(2) Raw Water Pump: In order to the raw water through the pretreatment filter, we install a raw warter pump
to increase the water pressure.
(3) Dosing Pump: The dosing pump can put the flocculant into the raw water. The flocculant can adsorb the suspended
solid in water, the flocculant together(coagulate) the suspended solid to big suspended solid. Let the suspended solid
easyly removed. The dosing pump in front of reverse osmosis membrane can put the scale inhibitor in the water. To
prevent the reverse osmosis membrane from blocking.
(4) Quartz sand filter: Quartz sand filter can remove the suspended solid in water. if your water contain more iron,
we will put the manganese sand to the bottle of Quartz sand filter. The manganese sand can oxide the iron and adsorption.
(5) Activated Carbon Filter: The activated carbon adsorb the color, odor and chlorine.
(6) Resin Systen(Filter): If your water is hard, your water contain the more calcium and magesium. The resin can lower the
content of the calcium and magesium in water. The principle is ion exchange.
(7) Brine Tank: The brine in the tank, the brine can remove the calcium and magesium. The principle is ion exchange.
(8) Precision Filter: The pp cartridge installed on the precision filter, The pore of pp cartridge is 1-5um. so that the precision
filter can remove the more small impurities to protect the reverse osmosis membrane.
(9) High Presure Pump: To increase the water pressure, let the water through reverse osmosis membrane.
(10) Reverse Osmosis Membrane: Because the pore of the reverse osmosis membrane is 0.1nm. The pore of the bacteria is
0.5-1um and the pore of the virus is 0.018-0.022um. So the reverse osmosis membrane can remove the bacteria and virus.
Also the reverse osmosis can remove lot kinds of the matter. for example: NaCl, CaCl2, MgSO4, NaF, NaCN(ph 11),
SiO2(50 ppm), NaHCO3, NaNo3, MgCl2, CaCl2, MgSO4,NiSO4, CuSO4, CuSO4, HCHO,AS.
(11) Oxygen Generator: Let the pure water become to oxygenated water.
(12) Ozone Generator: The ozone generator can keep the water fresh, and also can sterilize the water.
(13) Mixing Pump: To mix water and oxygen or ozone.
(14) Pure Water Tank: To store the pure water.